Square D 30/50 Pump Low Pressure Cut Off Switch
Square D Part: 9013FSG2J21M4
30/50 Square D Pump Low Pressure Cut Off Switch with lever
Settings: pump comes on at 30psi - pump goes of at off 50psi (*low pressure cut off feature)
*Disconnects pump if pressure drops below aprx. 20psi protecting pump from a run dry condition. A lever on the side of the pressure switch must be held upward manually until pressure in the line exceeds 20psi for initial pump operation.
HP Rated: 1-1/2HP @115V and 2HP@230V
Caution: There is live electrical current present in the switch that could cause injury or death. Adjust at your own risk.
Pressure Switch Adjustment Info
NOTE: A gauge is required in your system to make accurate ajustments. New adjustments arent configured while pump is running. You must run an additional cycle on and off to review your new settings on your gauge. Limit the amount of turns to about 4 turns up or down for each test. We always advise to take a measurement from the top of stud to top of adjusting nut before making any adjustment for a starting reference. That reference should be 3/4" fom top of stud to top of big nut #1 for a 40/60 setting. If using this switch with a HP rating over 2HP 230V you must use a Deluxe control box. This allows the switch to simply tell the pump to start and stop via a magnetic contactor coil at low amperage in the Deluxe type control box. Call 1-866-960-9621 if more info is needed.
Accessories ship FREE in 24 hrs. of order!